The short section of tube that attaches a sprinkler to the underground lateral pipe is called a “riser”. But the riser does much more than attach the sprinkler. It must hold the sprinkler in the correct position, it must allow you to adjust the sprinkler location, and we can also use it to protect the sprinkler from damage. The riser type you use is an important choice and deserves some attention. A good riser choice can save you time and money over the years. This article will take you through the many choices and the pros and cons of each. (“Lateral pipe” is the name given to the pipes that go from the zone valve to the sprinkler heads.)
PVC pipe that is exposed to sunlight should be painted to prevent sunlight from destroying the plastic. But what if you need to repair the PVC pipe later? You can’t glue pipe that has paint on it. In fact, you need to remove all of that paint from the area to be glued, even a small amount may cause leaks in the glued joint.
Using a small brush “paint” acetone onto the area of pipe where you want to remove the paint. (PVC primer will also work as a replacement for acetone, but the purple color makes it hard to make sure all the paint is off.) Allow the acetone to soak in for a few seconds then scrape off the paint with a knife blade or other metal edged tool like a putty knife. If some of the paint doesn’t easily come off re-coat the paint with more acetone. Once most of the paint is off, apply another coat of acetone. This time use a paper towel to wipe off the remaining paint. You may need to wipe down the PVC pipe 2-3 times with fresh paper towels to get a nice clean white surface. Now you can glue your joint using the normal method for gluing PVC pipe as described on the cement/glue can. The acetone will leave the pipe surface feeling sticky, that’s OK, you don’t need to wait for it to dry before you glue the joint. The primary ingredient in the purple PVC primer that is used to clean and prepare PVC pipe for gluing is acetone.
Q. My irrigation pump runs fine when the system is operating, but after it turns off it cycles on for 5 seconds every 10 minutes or so.
A. If you are using a pressure switch and pressure tank to turn the pump on and off my first guess would be that you have a water leak in your irrigation system. The water leaks out, which cause the water pressure to drop, then the pump kicks on and recharges the pressure. Then the pump shuts off again. That would cause exactly this symptom.
Knowing the problem is the easy part. Finding the leak, that could be harder to do. It could be a zone valve that isn’t turning off all the way or it could be a leaky pipe. You can narrow the search area a little, the leak will be someplace in the pressurized part of the system, that is, between the pump and the zone control valves. Start by looking for obvious dripping, then look for someplace that seems wetter than it should. If it is a leaky zone valve then the water will be leaking through the valve into the sprinkler zone pipes and will dribble out at the lowest sprinkler head. So look at the sprinkler heads. There will be a small “swampy” area around the lowest sprinkler head that is controlled by that valve.
Check The Dumb Stuff.
If the valve won’t open at all, or doesn’t fully open, start with the obvious things just to be certain. I know, any idiot knows better, but even us pros periodically overlook something really simple and obvious.
Tip: There are labeled photos of some of the more popular valve models showing the various valve controls (such as flow-controls, on/off levers, and bleed screws) mentioned in this article at this page: Anti-Siphon Valves with Parts Labeled.
- Is the water supply turned on?
- Is there a shut off valve on the water supply that may have been closed? Once I had a system I couldn’t get to work, couldn’t find any closed valves, but still no water to the sprinklers. Turned out the city water company had closed a valve in the street for street work they were doing and forgot to reopen it!
- Check the flow control on the valve to make sure it isn’t closed or partially closed. It is often desirable for the flow control to be left partially closed, but if it is restricting the flow too much that could be the problem. On some valves the flow control doesn’t have a handle, it is just a small screw in the valve lid. If unsure, look up your valve model at the manufacturer’s website to see if they have a drawing of the valve showing a flow control device location. Unfortunately, some inexpensive valves do not have a flow control device.
Manual Operation Test
Try manually opening the valve, using the on/off lever on top of the valve body. Some valves use a bleed screw to manually open them, so if you don’t see a lever labeled on/off or open/close, look for a screw, typically the screw has a knob handle to allow it to be twisted by hand. Do not fully remove a bleed screw! Just turn it about 1-2 to 1 full turn, water will squirt out from under the screw and the valve should open. Some valves have both a bleed screw and a on/off lever, on those valves I generally use the bleed screw as I have found it works better if the valve is being stubborn. If the valve opens correctly and fully when using the manual open lever or bleed screw, then the problem may be electrical. If the valve does not open fully when using the manual open feature, skip over the next section on electrical problems.
Basic Electrical Tests
If you don’t have a valve actuator test unit, start by making yourself a home-made valve activator using three nine-volt batteries. See my page with full instructions for making a irrigation solenoid valve activator (it’s easy and only takes about 2 minutes!)
Now use your actuator to test your solenoid and wires:
- NOTE: make sure you are using fresh, brand new batteries in your actuator! It takes a lot of amperage to open a valve and worn or old batteries won’t do the job. Don’t waste your time tracking down false results caused by bad batteries!!!
- Note #2: 24 VAC does not feel good if you shock yourself with it, especially if you are wet. Don’t touch bare wires without rubber gloves on!
- Disconnect the wires from the valve solenoid. Touch the valve solenoid wires to the terminals on your activator. The valve should open. If the valve fully opens then the problem is NOT the valve, the problem is with the wires leading from the controller (timer) to the valve, or possibly the controller is broken. Continue with the next step. If the valve does not open, then skip the rest of the electrical diagnosis items. The problem is with the valve or the valve solenoid.
- Controller problems are very rare, it is much more likely the problem is a broken wire. Do NOT try to test the controller by using a wire to create a short-circuit “spark” between the terminals! You may fry your controller! First reread the controller manual on how to wire the valve circuits and make sure you don’t have them wired wrong. Optional: You can test the controller using a multimeter if you have one and know how to use it. The controller output to the valves is 24 VAC. Most modern controllers will show a positive test for 24VAC even if the circuit is off, you need to test the circuit with a load. Don’t panic if you don’t know what that means or don’t have a multimeter. Just go to the next step.
- You can test the wire very simply. If the wires from the controller to the valve are disconnected from the valve reattach them to the valve solenoid now.
- Next remove the wires for the common and the “lead” wire circuit to your valve from the controller terminals.
- Attach your valve actuator to the 2 wires at the controller end, just like you did to the solenoid wires. The valve should come on. If it doesn’t open, or only opens partially, the wires from the controller to the valve are either damaged (cut or short circuiting), or you are testing the wrong wires. Are you sure you have the correct pair of wires for this valve? That’s often the problem with a newly installed system! It’s pretty easy to get the wires mixed up, especially if they do not have color-coded insulation. Another source of the problem may be damaged insulation on the buried wire. If the insulation on the wire has been removed or damaged someplace along the length of the wire it can cause a voltage leak. A nick or partial cut in the wire may cause resistance to the current in the wire. These wire problems cause the solenoid to not receive sufficient power to fully open the valve.
- If the valve does turn on fully the problem is the controller. Most modern controllers are not user repairable. If it is under warranty contact the manufacturer for instructions. They may ask you to do some additional tests. If the controller is not still under warranty you can contact a professional irrigation repair outfit for a repair quote. For most low-cost homeowner controllers it is cheaper to just replace the controller with a new one. If your current controller is not a Smart Controller you should consider replacing it with one. A self-adjusting Smart Controller will save you a lot of water and effort.
Valve Cleaning and Repair
If you’ve tested the controller and wires and they are OK, then the problem is with the valve itself. You have two choices: remove and replace the valve, or disassemble the valve to look for problems. Which way you go depends on which is easier for you to do. I generally try to clean the valve rather than replace it at this point.
Replacing a valve: Removing and replacing a valve can be a big job if the valve is fully installed. Basically this is a swap out, take a photo of the old valve before you remove it, then remove it and install the new one in it’s place. You probably will need to cut the pipe on the outlet side of the valve so you can turn the valve body to unscrew it from the inlet pipe and get it out. Some valves are installed so close together that you need to cut the pipe on both the inlet and outlet sides, this is especially true of anti-siphon valves. Once the old valve is out, you install a new one in the same location. Finally you need to repair the pipe if you cut it. If the pipe is PVC they make special couplers for repairing pipes that make the job easier. Remember to completely water proof all the wire splices!
Note: a lot of anti-siphon valves are not properly installed. Even sprinkler installation companies don’t use the care they should to insure correct installation, and a incorrect installation may be the source of your valve problems. See the article on How to Properly Install an Anti-Siphon Valve to help you get it in right this time!
Clean & Repair a Valve: Most people try to repair the valve rather than replace it. I really think a repair is often easier at this stage. If you do proceed with disassembling the valve be sure to notice how all the parts fit together so you can reassemble it when done. Tip: take photos of the valve and how the parts fit together as you disassemble it!
- If the valve is more than a couple years old you might want to purchase a repair kit for the valve make and model (see bottom of this page for examples of what to look for.)
- Turn off the water supply to the valve. Remove the solenoid by unscrewing it. Note: each manufacturer’s valve is slightly different, but the basics are the same. Your valve may look different from the Water-Master brand valve shown in these photos.
The bottom of the solenoid has a spring-loaded plunger in it. After removing the solenoid hold it in one hand and press the plunger in with your little finger. The plunger should spring back out when you release it and move freely in and out without catching or jamming as you press on it. If it doesn’t the solenoid is defective, see the manufacturer’s warranty info for how to proceed with replacement. If the solenoid is fine clean the bottom of the solenoid with a clean towel.
Next clean the little socket area in the valve lid that the solenoid screws into and make sure there aren’t any sand grains or bits of plastic loose in that area. Using compressed air (that canned air used to dust computer parts works great, some people can blow sufficient air with their mouths using a drinking straw…) gently blow air toward the ports (tiny holes) in the bottom of the solenoid socket. Keep the air outlet a couple inches away from the ports. Do not place the end of the air outlet against the ports! If you jam the air outlet down on them and blast air from a can or air compressor into the valve you will burst the rubber valve diaphragm inside the valve!!! You just want to gently blow any loose debris out of the ports and socket. Now screw the solenoid back on hand tight. Do not over-tighten it, do NOT use a wrench. It has a seal so you don’t need to crank on it to keep it from leaking. If you over-tighten the solenoid and force it too far in it will distort the plastic and the plunger will jam. Now with the solenoid back on, don’t bother to rewire it yet. Turn on the water and check to see if the valve works manually. Sometimes the solenoids aren’t installed correctly and this is all it takes to fix the problem. If the valve now works rewire it and you’re done. If the valve still doesn’t work go to step 2.
- Remove the solenoid again. Now remove the valve’s lid or cap. The lid or cap may screw off like a jar lid, or it may be held in place with screws. If it is the jar lid type you may need a strap wrench to remove the lid. (They market these jar lids as “easy to remove”, I’ve found few of them actually are.)
A rubber diaphragm sits under the cap and there is a spring between it and the cap, watch for the spring that it doesn’t get lost. Be very careful not to let dirt get into the valve body while the cap is off, put a piece of kitchen cellophane wrap or something similar over it to keep out dirt.
- Once the cap is removed look at the cap. There are tiny holes, called ports, that go from under the solenoid to the bottom side of the cap/lid. Make sure none of those ports are blocked by a bit of manufacturing plastic or dirt. You can use a tiny piece of wire to clean them, be very careful not to scratch the plastic or enlarge the hole. Sometimes one of the ports is not drilled all the way through. In that case the valve is defective, see your warranty information for how to replace the valve. I have known people who have successfully used a tiny drill bit held in their hand to very carefully drill a blocked port clean. If you are very careful this may work, BUT it may void your valve’s warranty! One guy had 6 valves all with the same partially drilled port, clearly a manufacturing error. He drilled them by hand and every one of them worked afterward. Your call on that one.
- The lid or the diaphragm may also have s small screen filter built into it. Look carefully they are small and hard to see. This is a feature found primarily on a few more expensive brands. At the time I am writing this most Rainbird valves have a tiny filter molded into the diaphragm, so if it is a Rainbird valve be sure to look for it. If there is a screen be sure it isn’t clogged up. A toothbrush works good for cleaning the screens.
- Check the rubber diaphragm for any cracks, tears, rips, or holes in it. It should be flexible and in very good condition. If not, replace it. Repair kits with replacement diaphragms are sold at some hardware stores, all irrigation stores, or may be obtained online.
- Reassemble the valve when you are finished cleaning the parts and checking for blocked ports. Everything goes back in the same place it came from. Be very careful not to get dirt into the valve when reassembling it. Lubricate all the o-rings using standard KY Jelly (not the heating/stimulation types.) Do not use oil or silicone lubricants! KY Jelly is water-based and will not destroy the rubber seals like oil based products will.
- It should work correctly now.
Ads for Typical Repair Parts:
(Amazon has lots more repair parts, for many brands, this is just a start! Hardware & home improvement stores in some areas also carry valve repair parts for a few common models. Dedicated irrigation stores usually stock common brand parts and can order just about any brand or model.)
Q. I just restarted my sprinkler system after it had been winterized. When I turned on the water to the system, all the valves stations came on at once, as if by-passing the timer unit. Even when I turn the timer unit Off, the sprinklers keep running.
A. This is a common problem when restarting after your sprinkler system has been winterized, or after the system has been turned off for an extended period of time. It also often occurs with brand new solenoid valves that have just been installed. There are a couple of possible problems that can cause this, so we’ll look at a couple of solutions. One of the tricks below should get your irrigation valves opening and closing properly again.
Air Trapped in the Valve:
The valves may have air trapped in them. A small bubble of air becomes trapped in the tiny water ports of the valve, this stops the water from flowing through the port. Since the water flowing through the port is what holds the valve diaphragm closed, the valve stays open.
1. Turn on the main water supply.
2. Now go to the individual valves and using the manual open & close control on the valve. The manual open & close control is either a lever on the valve (most often it is under the valve’s solenoid), or it may be a screw on the top of the valve bonnet. If it is a screw don’t fully remove it, just open it until water starts squirting out. Set it to open, wait a few seconds, then set back to closed. If the valve doesn’t close within a minute, try it again. It may take several tries to get the air bubble to “burp” itself out. Try tapping the valve to dislodge the air while the valve is open if needed. Note: old plastic valves may become brittle and crack when tapped, so if the valve is plastic and old don’t tap on it except as a last resort if the air doesn’t come out.
3. If that doesn’t fix the problem, you can almost always force the air out using the manual flow control on the valves. Unfortunately, some inexpensive valves do not have a flow control. The flow control is a handle, similar to what a manual valve has, that is on the top of the valve. It works just like a regular faucet, turn clockwise to close. Most flow controls have a hand operated flow control, others have a cross handle that is turned using a tool (pliers will work if you don’t have the special valve opening tool.) A few valves have a screw for the flow control that requires a screwdriver to turn. Try completely closing and then reopening the manual flow control on each valve. That should force the air out and fix the problem.
Valve Needs to be Throttled:
If air in the valve doesn’t seem to be the problem it is possible that your valves don’t have enough pressure differential and they need to be throttled in order for them to close by themselves.
Here’s how to throttle them using the flow control adjustment:
Note: some inexpensive valves do not have a flow control adjustment feature on them. If that is the case you are not going to be able to do this. You will need to replace the valve with a better quality valve that has a flow control.
1. Use the manual flow control on each valve to close all of the valves. Now the main water supply should be on, but none of the valves should be allowing water through. So no sprinklers are running.
2. Start with just one valve at a time. Rotate the manual on/off lever to the on position. Open the manual flow control knob all the way (turn as far as it will go counterclockwise). The valve should come on and sprinklers run.
3. Next rotate the manual on/off lever under the solenoid to the closed position. The valve should close (it may take it a minute or two to close) but probably won’t, because that is the problem, they won’t close! If the sprinklers turn off the valve is working correctly, go to the next valve and start again with step #2. If the valve does not close by itself, you need to throttle the valve. Continue to step #4.
4. To throttle the valve you partially close the flow control knob. Start by turning it one full turn clockwise. Wait a minute for the valve to close. If it doesn’t close, turn the handle another half turn clockwise. Wait again. If the valve still doesn’t close turn it another half turn. Keep doing this, at some point the valve should suddenly make a whooshing noise and close. If the valve is broken it will never close by itself and eventually as you close the flow control more and more the sprinkler radius will start becoming noticeably reduced. If that happens you need to repair or replace the valve. But in most cases the valve will close by itself after you have partially closed the flow control. It might take 4-5 complete turns before this happens.
You shouldn’t see any significant change in the sprinkler performance with the valve flow control in the partially closed position, except that the sprinklers may mist a little less (which is a good thing.) This is called “throttling the valve” and some valves won’t close by themselves unless they are throttled. The way a solenoid valve works is that the pressure differential as the water goes through the valve is what the valve uses to power itself into the closed position. If there isn’t enough pressure differential the valve will not close by itself. Often there is not enough pressure differential when there aren’t very many sprinklers on the valve circuit. When you throttle the flow control you are simply increasing the pressure diferential.
You can leave the flow control in a partially closed position permanently, it will not hurt the valve. The valve is designed to allow you to do this. The sprinklers should still operate well as the amount of water throttled when you partially close the valve is not significant.
For valve repair instructions see how to fix a solenoid irrigation valve.
Q: The pressure is blowing off the pipes/tubes from the barbed fittings on my drip irrigation system. This is only happening on hot days (30°C=86°F in the shade). Pipe temperature could be as high as 45°C=113°F. Our water pressure varies between 2.5 and 3.1 bar (35 and 45 PSI.)
A: Drip tube should not blow off the barbs, even on a hot day when the temperature softens the plastic tubing (however the heat does make it easier for them to blow off!) There are three common reasons the tubes blow off.
1. The most common problem is that the water pressure is too high. This is probably your problem. The water pressure should be around 1.3 to 2.0 bars (20 – 30 PSI). You should install a pressure reducer after your valve to lower the pressure.
2. The pipe and fittings may not be the same size. This is one of the pitfalls I warn about in my Drip Guidelines. 16mm and 18mm tube are both commonly referred to as 1/2 inch in the USA! The fittings for these two are not interchangeable.
3. Pressure spikes can pass through the less expensive pressure reducers often sold for drip systems. If you have high water pressure this may be the problem. The solution is to install a high quality brass pressure reducer valves. These generally are sold in the plumbing department rather than the irrigation department of stores and cost $50.00 or more.